- OD: 10.2mm-720mm
- WT: 1.2mm~12mm
- Length: 5-12m or as to customer requirement
- Surface: Painting, oil coating, Anti-corrosion & Insulation.
- Delivery state: Hot Rolled, Cold Drawn.
- Steel Grade: P195GH, P235GH, P265GH, 16Mo3, 14MoV6-3, 13CrMo4-5, 10CrMo9-10.
Alloy Steel Pipe EN10216-2 Grade Available Specification
If you want to learn more, please free to contact us and request a free sample and quote, etc.
|Product Name||Executive Standard||Dimension (mm)||Steel Code / Steel Grade|
|Seamless Ferritic Alloy Steel Pipes for High Temperature Use||EN10216-2||Ø8″~42″ x WT15~100||13CrMo4-5, 1-CrMo9-10, X10CrMoVNb9-1, 15NiCuMoNb5-6-4|
EN10216-2 is a specification for seamless steel pipes for specific high temperature applications such as boiler tubes and power plants. It has the following steel grades: P195GH, P235GH, P265GH, 16Mo3, 14MoV6-3, 13CrMo4-5, 10CrMo9-10, including non Alloy and alloy steel. EN 10216-2 specifies the technical delivery conditions for 2 test categories for circular section seamless pipes, ANSON is an experienced supplier of boiler and pressure steel pipes that can supply you with EN10216-2 pipes in all grades and size ranges .
Inspection and Test For EN 10216-2 Alloy Steel Pipe
|Inspection and test type||Test frequency||Test category|
|Mandatory tests||Ladle analysis||One per ladle||1||2|
|Tensile testing in room temperature||One per every test pipe||X||X|
|Flattening test for D<600mm and the ratio of D≤0.15 but T≤40mm or ring testing for D>150mm and T ≤40mm||X||X|
|Rolling test on a mandrel bar for D≤150mm and T≤10mm or ring testing for D≤114,3mm and T ≤12,5mm||X||X|
|Resilience testing at the temperature of 20 ºC||X||X|
|Tightness testing||Every pipe||X||X|
|NDT in order to identify longitudinal discontinuity||Every pipe||X||X|
|Material identification for alloy steel||X||X|
|Optional tests||Final product analysis||One per ladle||X||X|
|Tensile testing at elevated temperature||One per ladle and for the same thermal processing conditions||X||X|
|Resilience testing||One per every test pipe||X||X|
|Resilience testing in the machine direction at the temperature of -10ºC for non-alloy steel grades||X||X|
|Wall thickness measurement at a distance from pipe ends||X||X|
|NDT in order to identify transverse discontinuity|
|NDT in order to identify delamination||X||X|